Standard Number: GB 50116-2013
Title: Code for design of automatic fire alarm system
Language: Simplified Chinese
Replacing Standard: GB 50116-1998
Publication Date: 2013/9/6
Execute Date: 2014/5/1
Publisher: Chinese Standards(GB)
Number of Pages:136
Description:This specification applies to new, expanded and rebuilt the building and structures set in the design of automatic fire alarm system, does not apply to the production and storage of gunpowder, explosives, munitions, initiating explosive device and other places set up the design of automatic fire alarm system.
1, the increase in residential building fire automatic alarm system, combustible gas detection alarm system, electric fire monitoring system related design rules.
2, increase road tunnels, oil Tank farm, cable tunnel and height is greater than 12 meters Spaces of automatic fire alarm system related design rules.
3, cancellation, chapter 3 system protection object classification and fire detector set parts.
4, the original chapter 4 (alarm region and detection region division), (design) system in chapter 5 and chapter 6 (fire control room and fire linkage control) content is merged into a new chapter 3 (design) system.
5 , increasing the area display, module, graphic display device, fire alarm equipment such as transmission equipment or user information transmission device set rules.
: 1 general 2 term 3 system protection object classification and fire detector set parts 3.1 system protection object classification 3.2 fire detector set part 4 alarm region and detection region division 4.1 alarm regional division 4.2 detection area was divided into 5 system 5.1 general provisions
of 5.2 meter system selection and design requirements in the form of 5.3 integrated fire control design requirements for fire emergency broadcasting 5.5 5.4 fire fire alarm device for 5.6 * 5.7 phone system grounding 6 fire control room and fire linkage control. 1 general provisions 6.2 fire control room 6.3 the function of fire control equipment and the choice of fire detector 7.1 7.2 points under general type of fire detector choose 7.3 linear detector chooses 8 fire detector and manual fire alarm button set of 8 . 1 point type fire detector set number and arrangement of 8.2 linear detector set 8.3 manual fire alarm button set 9 system power supply
wiring 10 10.1 general provisions 10.2 house wiring appendix A detector installed distance limit curve of appendix B the influence of different height room beam of detector set as defined by the beam area appendix C a detector protection area of the beam between the number of appendix D set specific parts of the fire detector (recommended) d. 1 extra protection object d. 2 D level of protection objects. 3 secondary protection object Appendix E this specification language suggests that additional instructions
: PDF(Acrobat Reader) or Word version doc
Tile in English: Code for design of automatic fire alarm system